The Storz adapter
shall have a hard anodized aluminum Storz ramps and lugs. The adapters
finish shall be hard coat anodized to Mil-A-8625f, Type 3 dark grey. The
adapter shall be made of forged or extruded 6061-T6 aluminum and secured to
the nozzle by 2 stainless steel set screws, inserted 1800
apart. The female adapter shall contain a flat rubber gasket which
seals against male hydrant nozzle.
The blind cap shall have hard
anodized aluminum Storz ramps and lugs, made of forged or extruded 6061-T6
aluminum. The center cap shall be equipped with a suction seal. The cap
shall be connected to the adapter or the hydrant with a 1.125" vinyl coated
aircraft cable. Once installed, the 5" Permanent Hydrant Adapter with cap
extends 2.9" from the hydrant nozzle.